Encyclopedia of Life: Tips for Solving Faults in Biopharmaceutical Purified Water Treatment Equipment
Life Encyclopedia: biopharmaceutical purification water treatment equipment troubleshooting tips Author: When it comes to the biopharmaceutical industry everyone is familiar with, biopharmaceutical product quality requirements more stringent, this will also influence many lives. The water used in the biopharmaceutical industry is generally purified water. Therefore, biopharmaceutical purified water treatment equipment is widely used in the pharmaceutical industry, using newer processes such as reverse osmosis and EDI. We understand that the biomedicine and other industries will encounter problems when applying purified water equipment, not only equipment problems, but also manual problems. So how should we deal with failures? When using biopharmaceutical purified water Pay attention to maintenance and maintenance when handling equipment. Under normal circumstances, due to long-term operation, the standardization flux and system delay rate will decrease, and the operating pressure will increase. When this happens, it means that the pharmaceutical purified water equipment needs to be cleaned. When cleaning, pay attention to the relationship between the frequency and the pretreatment degree of the system. Generally, when the pretreatment degree of the system is less than three, the frequency of cleaning is It is enough to maintain the degree of four times a year, but if the pretreatment degree of the system is greater than three, the degree of cleaning will be doubled. Pharmaceutical purified water equipment should pay attention to the downtime limit during use. If the water temperature is higher than 20 degrees but less than 40 degrees, the more downtime can be up to four hours, if it is below 20 degrees, then it will be shut down. The time can be extended to 8 hours. Faults and treatment methods of biological pharmacy purified water treatment equipment: 1. Reasons for the low flow rate of the first-grade pure water: it may be that the security filter element is blocked (then the security filter element is replaced), and the first-level booster pump may not be pressurized (Repair the first-level booster pump), the membrane may be fouled or contaminated (the RO membrane is treated), or the first-stage RO flushing solenoid valve may be damaged and it is in a long open state (replace the RO membrane). 2. The reason for the high first-level conductivity: it may be membrane fouling or contamination (then treat the RO membrane, clean or replace the RO membrane). 3. The reason why the system does not produce water: It may be that the pre-conditioner is blocked, the high-pressure pump enters the low-pressure protection, and the raw water pump is started to observe the pressure difference of each pretreatment level (clean the pretreatment or replace the tight filter element). It may be that the low-pressure switch is damaged (repair or replace the low-pressure switch) 4. The original water tank has water overflow: it may be that the high water level switch of the original water tank is damaged (repair or replace the water level switch) 5. The high-pressure pump cannot be stopped or the pure water tank has water overflow Reason: It may be that the high water level switch of the pure water tank is damaged (repair or replacement of the water level switch. The environmental protection water treatment equipment company reminds you: Our company provides you with high-quality purified water equipment, as well as a full range of services. Let you use More at ease, if you are interested, please pay attention to our website.
Contact Person: Ms.Carrie Chan
TEL : (+86)020-39185731
E-MAIL : firstname.lastname@example.org
Whatsapp/Wechat : +86-13751887537
Water Treatment System Add:9A,Building 8,Lianfa Industrial Park , Luopu Street, Panyu District, Guangzhou City, China
Water Filter Cartridge Add:Zhangcun village,Daze town, Xinhui district, Jiangmen City, Guangdong, China
Sign up for our newsletter
Get the latest news and updates from the leaders in water treatment and process separation.