What are the advantages, operation and maintenance and fault inspection of stainless steel integrated pure water treatment equipment?
What are the advantages, operation and maintenance and fault inspection of stainless steel integrated pure water treatment equipment? Author: rapid economic development to the environment had a negative impact on people's air, water and soil have suffered unprecedented pollution, water pollution is a problem in which people are most concerned about. Therefore, many people have purchased stainless steel integrated pure water treatment equipment to improve water quality, which is convenient and simple to install and saves costs. Stainless steel integrated pure water treatment equipment is the main water supply system in the industry. Once the equipment fails, it will inevitably affect production efficiency. What are the common faults and solutions of stainless steel integrated pure water treatment equipment? 1. Low product water resistivity: produced Reasons: ① Power supply: the point is extremely out of power, the voltage setting is too high or too low, one or more electrode connectors are loose, and the electrode polarity is reversed. ②Water flow: the water flow through the module is lower than the minimum, and the water flow through the module is higher than the maximum. ③Water intake: does not meet the requirements of water intake regulations. ④Module: blockage or fouling. ⑤Module torque: the torque is too small. Remedy: ①Turn on the power supply, check the electrode voltage, ensure that the electrode is connected properly, and ensure that the electrode polarity is correct. ②Re-adjust the pressure of concentrated water, extreme water and inlet water. ③Check the quality of RO water, especially TDS, CO2, etc. ④Clean the module. ⑤Re-adjust the torque. 2. Low production water flow: Cause: ①Fresh water chamber: fouling. ② Water inlet pressure: too low. ③Temperature: too low. Remedy: ①Check the concentration of organic pollutants in the influent water, and whether there is a pre-filter to prevent impurities from entering the EDI. ②Increase the water flow rate. ③Pay attention to the viscosity of the water at the inlet temperature. 3. There is no concentrated water or the concentrated water flow is low: Cause: ①The relevant valve is not set properly. ②Scaling in the fresh water chamber. Remedy: ①Adjust the valve to increase the flow. ②Check the TDS, hardness, and pH value in the RO product water. 4. The module overflows with too much gas, and the pH value of the produced water is too high or too low: Cause: the voltage setting is too high. Remedy: reduce the voltage 5. Causes of excessive current flowing through the module: ①The conductivity of the inlet water is too high high. ②No water flows through the module. Remedy: ①Check the TDS in the RO product water. ② Make sure there is water flowing through the module, otherwise the module will be damaged. The above is the introduction to the common faults and solutions of stainless steel integrated pure water treatment equipment. I believe that everyone has a certain understanding of the common fault solutions of stainless steel integrated pure water treatment equipment. The maintenance of stainless steel integrated pure water treatment equipment is Very importantly, if you have other problems during use, you can also contact us at any time.
Contact Person: Ms.Carrie Chan
TEL : (+86)020-39185731
E-MAIL : firstname.lastname@example.org
Whatsapp/Wechat : +86-13751887537
Water Treatment System Add:9A,Building 8,Lianfa Industrial Park , Luopu Street, Panyu District, Guangzhou City, China
Water Filter Cartridge Add:Zhangcun village,Daze town, Xinhui district, Jiangmen City, Guangdong, China
Sign up for our newsletter
Get the latest news and updates from the leaders in water treatment and process separation.