What are the correct steps for installing pure water treatment equipment in small and medium-sized laboratories?
What are the correct steps for installing pure water treatment equipment in small and medium-sized laboratories? Author: small and medium sized laboratory water treatment equipment to follow to improve productivity, improve the effect of the application of the principle of equipment to provide the best water treatment solutions for small and medium sized laboratory water to meet the industry demand for water. Pure water treatment equipment installation steps for small and medium-sized laboratories: 1, unpacking acceptance confirmation Open the box for inspection of the various components of the small and medium-sized laboratory pure water treatment equipment, and carefully check whether the components are fully equipped. Confirm whether the specifications and materials of the equipment accessories meet the standards. Organize technical materials and instructions and create files. Small and medium-sized laboratory pure water treatment equipment and installation confirmation of the instrument used After installing in strict accordance with the design drawings and technical data, check whether the components are installed correctly and whether the design specifications are reasonable. Because the laboratory has strict water requirements and must be equipped with high-precision meters, it is necessary to check whether the data displayed by the meters are accurate. 3. Confirmation of the installation of the pipeline distribution system In order to prevent the breeding and pollution of bacteria in the pipeline from polluting the pure water during the transportation process, the materials selected for the pipeline must be non-toxic and corrosion-resistant. And in the installation process, try to ensure that there are no dead ends to prevent the breeding of microorganisms. 4. Passivation treatment of storage tanks and pipelines In order to ensure that the pure water produced will not be subjected to secondary pollution during transportation, and to avoid the presence of other oily or ion pollutants on the inner walls of the storage tanks and pipelines, it is necessary to treat the pipelines and water storage tanks. Perform passivation treatment. Ensure that the pure water fully meets the standard when it is input to the point of use. 5. The installation of the air-cooled ozone generator confirms that the ozone generator has a sterilization and disinfection effect on the hospital pure water device, so in order to ensure the quality of the water, the device must be installed on the self-circulating pipe on the side of the pure water tank to achieve the sterilization effect . The purified water equipment designed by the Research Institute of Environmental Protection Small and Medium-sized Laboratory Pure Water Treatment Equipment meets GMP certification requirements and other requirements such as FDA.
Contact Person: Ms.Carrie Chan
TEL : (+86)020-39185731
E-MAIL : firstname.lastname@example.org
Whatsapp/Wechat : +86-13751887537
Water Treatment System Add:9A,Building 8,Lianfa Industrial Park , Luopu Street, Panyu District, Guangzhou City, China
Water Filter Cartridge Add:Zhangcun village,Daze town, Xinhui district, Jiangmen City, Guangdong, China
Sign up for our newsletter
Get the latest news and updates from the leaders in water treatment and process separation.