What are the installation steps of RO reverse osmosis pure water equipment?
What are the installation steps of RO reverse osmosis pure water equipment? Author: Water is the source of all things, whether it is daily life and industrial production, must rely on water, we can say that our life has entered a water treatment era. Many companies require pure water in production, and ultra-pure water is undoubtedly the most suitable for demand, so many users will use RO reverse osmosis pure water equipment. Nowadays, RO reverse osmosis system is very powerful, which will exist in various water treatment equipment, and it also occupies a very important position in pure water equipment. In order to let the friends who just bought RO reverse osmosis pure water equipment install the equipment faster, the following briefly introduces the installation of RO reverse osmosis pure water equipment. 1. When choosing the installation location, you should take into account the location of the pre-treatment installation device. 2. No valve or any device that prevents the outflow of pure water can be installed in the pure water outlet connecting pipeline. 3. The system should be placed in a place that is convenient for operators to enter and maintain, and there should be ample space around it. 4. The equipment should be installed in a dry place, because long-term exposure to a humid environment will cause damage to electrical components and equipment. 5. The installation of electrical appliances must be carried out by qualified electrical technicians and workers, and reliable grounding must be provided. 6. The diameter of the pure water connection pipe and the sewage discharge pipe should not be smaller than the diameter of the pure water outlet and the sewage outlet. 7. The equipment does not need a special fixing method, just adjust the height of the feet carefully. The equipment with universal transmission can be locked after adjusting the height. 8. After the pretreatment and the host are in place as required, connect them with PVC, ABS or stainless steel pipes. A sewage outlet should be installed at the inlet of the main engine. 9. The installation site should ensure that the ambient temperature in summer is not higher than 45℃, and in winter it is not lower than 4℃. Otherwise, it will cause irreversible damage to the equipment.
Contact Person: Ms.Carrie Chan
TEL : (+86)020-39185731
E-MAIL : firstname.lastname@example.org
Whatsapp/Wechat : +86-13751887537
Water Treatment System Add:9A,Building 8,Lianfa Industrial Park , Luopu Street, Panyu District, Guangzhou City, China
Water Filter Cartridge Add:Zhangcun village,Daze town, Xinhui district, Jiangmen City, Guangdong, China
Sign up for our newsletter
Get the latest news and updates from the leaders in water treatment and process separation.