What are the quick and accurate operating steps for the installation of automatic boiler softening water treatment equipment?
What are the quick and accurate operating steps for the installation of automatic boiler softening water treatment equipment? Author: industrial boiler is now common social equipment, automatic boiler softened water treatment equipment is the use of pre-treatment method, reverse osmosis technology, softened water treatment and post-treatment stages, the water conductive medium almost completely removed, turn the water separated Water treatment equipment that removes decomposed colloidal substances, gases and organic matter to a very low level. So, what are the precautions when installing boiler automatic softening water treatment equipment? (1) Punch holes or fix the boiler automatic softening water treatment equipment at the selected position. The holes must be smooth, the depth and distance of the holes must be accurate, and the hole circumference must not have cracks, nicks, or burrs. (2) Connect to the tap water pipe, first close the tap water main valve, connect the boiler automatic softening water treatment equipment, the interface should be wrapped with raw tape to prevent water leakage. (3) Connect the concentrated water outlet, the boiler automatic softened water treatment equipment can put the sewage pipe directly into the sewage pipe, and leave a certain space at the port to prevent sewage from flowing into the equipment and prevent the 'siphon' phenomenon of the sewage outlet. The sewage pipe of the equipment is directly put into the sewage pipe, and a ball valve should be installed at the end of the sewage pipe. It can be opened from time to time to discharge sewage. The sewage pipe can also be directly connected to the original tap. The sewage pipe and the equipment sewage outlet must be connected properly to prevent water leakage. (4) Connect the water outlet and the faucet. If the flow rate is greater than 500 liters, you can directly use the 4-division pipe and the universal faucet. If the flow rate is less than 500 liters, you can choose to connect the purified water outlet with a 4-to-2 connector, and connect to the purified water outlet through a 2-point white PE tube 2 tap connection. When connecting the second pipe, first cut the pipe port flat, then put on the nut, then insert the pipe plug into the PE pipe, insert it tightly, insert the PE pipe about 1cm beyond the nut into the joint and tighten it. (5) Install the faucet. If you want to install the faucet on the sink, the stainless steel sink can be opened with a hole opener. If you want to fix the faucet on the wall, you can use the right-angle faucet hanger to fix the faucet on the wall. The connection method of the joint is the same as (4), and the fixed part must be tightened without shaking. (6) Open the main water inlet ball valve and debug the water purification device (see Maintenance and Maintenance for details of the debugging steps), and observe whether the joints are leaking. The observation period is at least 2 hours. A clean dry towel can be placed under the water purification device for inspection. Whether there is water seepage phenomenon. The above are the precautions for the installation of the environmental protection boiler automatic softening water treatment equipment, I hope it will be helpful to everyone.
Contact Person: Ms.Carrie Chan
TEL : (+86)020-39185731
E-MAIL : firstname.lastname@example.org
Whatsapp/Wechat : +86-13751887537
Water Treatment System Add:9A,Building 8,Lianfa Industrial Park , Luopu Street, Panyu District, Guangzhou City, China
Water Filter Cartridge Add:Zhangcun village,Daze town, Xinhui district, Jiangmen City, Guangdong, China
Sign up for our newsletter
Get the latest news and updates from the leaders in water treatment and process separation.