What data need to be recorded when the integrated reverse osmosis pure water treatment equipment is running?
Integrated reverse osmosis water need to record what data processing equipment to run the article:? As we all know, the integration of reverse osmosis water treatment equipment uses a unique reverse osmosis water filtration technology, heavy metals, bacteria and other microbial impurities. Producing high-quality pure water not only meets the water demand of enterprises, but also ensures the safety of people's drinking water. With the development of technology, the automatic control of integrated reverse osmosis pure water treatment equipment program has made many users feel very convenient. After the user purchases the integrated reverse osmosis pure water treatment equipment, the supplier will remind the user that the integrated reverse osmosis pure water treatment equipment needs to make an operation record during the operation. What is the significance of the operation record? What data are included? The statistics of the operation record data of the integrated reverse osmosis pure water treatment equipment can provide some basic information for equipment maintenance and overhaul, so as to find out the cause of equipment failure more quickly. The detailed operation record data includes the following points: 1. Start-up record The characteristics of the RO system of the integrated reverse osmosis pure water treatment equipment must be recorded from the beginning of its use. The start-up report should include a complete description of the device, and a flow chart can be used. Equipment RO reverse osmosis system and post-treatment, initial pre-treatment, and RO performance record. All meters and meters must be calibrated and recorded in accordance with the manufacturer's recommendations. 2. RO operating data The operating data can reflect the working performance of the RO system of the integrated reverse osmosis pure water treatment equipment. All data must be recorded during the operation of the entire RO system. These data can be used for the analysis and evaluation of the RO system of the purified water equipment. Performance provides information. 1. Flow (flow of product water and concentrated water in each section). 2. Pressure (all levels of water supply, concentrated water, product water). 3. Temperature (water supply). 4. PH value (feed water, product water, concentrated water). 5. Electrical conductivity (feed water, product water, feed water for each section, concentrated product water). 6. Operating hours. 7. Incidents (SDI, PH value and pressure aberrations, outages, etc.) 8. All instruments and meters must be proofread (revised) at least once every three months or half a year. 9. Flow pressure, temperature, PH value, conductivity, SDI (water supply), once a day. 10. The TDS of each section of feed water, concentrated water, and product water is analyzed once a month. 11. Use steam to clean the activated carbon filter and the disinfection of the stainless steel pipeline every week. Having mastered the above-mentioned best integrated reverse osmosis pure water treatment equipment operation record data project, I believe you will be able to better grasp the equipment maintenance cycle in the future and make the equipment more convenient to use. For more knowledge about the daily maintenance of integrated reverse osmosis pure water treatment equipment, please visit our website frequently, and we will update relevant technical information frequently.
Contact Person: Ms.Carrie Chan
TEL : (+86)020-39185731
E-MAIL : firstname.lastname@example.org
Whatsapp/Wechat : +86-13751887537
Water Treatment System Add:9A,Building 8,Lianfa Industrial Park , Luopu Street, Panyu District, Guangzhou City, China
Water Filter Cartridge Add:Zhangcun village,Daze town, Xinhui district, Jiangmen City, Guangdong, China
Sign up for our newsletter
Get the latest news and updates from the leaders in water treatment and process separation.