What is the correct cleaning method for small and medium stainless steel pure water equipment?
What is the correct cleaning method for small and medium stainless steel pure water equipment? Author: Because of the national economy and raise the level of water pollution exacerbate both these problems, many families abandoned the original drinking water, the installation of small and medium stainless steel water equipment of choice for many consumers. The editor here wants to remind everyone that small and medium-sized stainless steel pure water equipment will come into contact with a large number of pollutants in the water during long-term use, resulting in some pollution of the small and medium-sized stainless steel pure water equipment itself. Therefore, users need to clean the small and medium-sized stainless steel pure water equipment regularly. Water equipment. So, how should small and medium-sized stainless steel pure water equipment be cleaned? Read this article to learn about the cleaning methods of small and medium-sized stainless steel pure water equipment. 1. Prepare the cleaning liquid in the cleaning water tank according to the selected cleaning agent formula, circulate the cleaning liquid with a pump, and stir it evenly for later use. 2. Close the water inlet and outlet valves and discharge valves on the reverse osmosis device, and open the chemical cleaning inlet and outlet valves on the reverse osmosis device to form a circulating cleaning system. 3. After connecting the cleaning pipeline, turn on the power switch of the water treatment cleaning pump, and clean it for 1-2 hours according to the specified flow, pressure (0.14-0.22Mpa) and temperature (<30℃) (if necessary, soak 1-2 Hours), the initially discharged cleaning liquid is discharged into the trench to ensure the concentration of the cleaning liquid. 4. After cleaning, drain the remaining liquid from the cleaning water tank and inject water that meets the water inlet index of the water treatment reverse osmosis device, and rinse under the same cleaning conditions. Or use a raw water pump to flush under similar low-pressure flushing conditions. 5. After each stage of flushing is completed, low-pressure flushing and high-pressure operation are carried out according to the specified operation mode. Initially, the produced water is discharged into the trench, and then enters the product water tank when the outlet water index is qualified. 6. After cleaning, the chemical cleaning device must be rinsed. Never put the cleaning filter, cleaning pump and other equipment in the condition of cleaning fluid. The above is the most correct cleaning method for small and medium stainless steel pure water equipment. Users can refer to this article for regular cleaning of small and medium stainless steel pure water equipment. To ensure the long-term and stable operation of small and medium-sized stainless steel pure water equipment, in addition to the quality of the equipment itself, regular maintenance is also very important.
Contact Person: Ms.Carrie Chan
TEL : (+86)020-39185731
E-MAIL : email@example.com
Whatsapp/Wechat : +86-13751887537
Water Treatment System Add:9A,Building 8,Lianfa Industrial Park , Luopu Street, Panyu District, Guangzhou City, China
Water Filter Cartridge Add:Zhangcun village,Daze town, Xinhui district, Jiangmen City, Guangdong, China
Sign up for our newsletter
Get the latest news and updates from the leaders in water treatment and process separation.