What is the daily maintenance and maintenance of small and medium-sized industrial water softening equipment?
What is the daily maintenance and maintenance of small and medium-sized industrial water softening equipment? Author: Due to the serious water pollution, water production has been questioned many companies, small and medium industrial water softening equipment, also known as softeners, softener and softened water treatment equipment. Water softening equipment mainly uses sodium ions to remove dissolved minerals, calcium and magnesium ions and sulfates in water. It is widely used in industrial boilers, air-conditioning circulating cooling water and food process water. Environmental protection reminds users that using small and medium-sized industrial water softening equipment must be carefully maintained and maintained to extend the service life of the equipment. The specific points are as follows: 1. The equipment must be kept clean during use, and the equipment must be wiped with a clean cloth frequently. To ensure that there is no water outside the equipment. 2. The pipeline should be installed with strong support to prevent the control valve from being forced. 3. For small and medium-sized industrial water softening equipment that has not been used for more than half a month, the drain pipe must be lifted to the exchange tower and the water in the pipe must be drained clean. When the water inlet pipe of the softener is connected to the domestic water pipe, a backflow prevention valve should be installed on the water inlet pipe. 4. When not in use for a long time, it is necessary to clean the brine from the exchange tank and the salt tank, and add emulsified oil to each valve to prevent rust. In summer, when the equipment is not used for more than half a month, the start-up time should be extended to 1 hour to 2 hours to prevent the resin in the exchange tank from moldy and produce bacteria and microorganisms. 5. Check whether the small and medium-sized industrial water softening equipment is fixed on the horizontal surface, and the sewage drain pipe is close to the sewer. When the inlet water pressure is lower than 0.15MPa, pressure measures should be taken. 6. The length of the sewage pipeline should be less than 6 meters, and no valve should be installed on the pipeline; the outlet should not be higher than the valve body, and the terminal should be open to avoid siphoning. 7. When the equipment is working, it should provide power and water supply at the same time. Remember: cut off the power supply and perform maintenance and operation. 8. The length of the drain pipe of small and medium-sized industrial water softening equipment should be less than 6m. There is no valve installed on the pipe, and the outlet should not be higher than the valve body and terminal opening to avoid siphoning. 9. Anti-scaling The thermal conductivity of scale is very poor, which is hundreds of times different than that of metal. Therefore, the temperature of the fouling part is too high, causing the metal to drop in strength, local deformation, bubbling, and even explosion accidents, endangering life and safety. 10. Prevent salt accumulation The salt accumulation of the superheater will cause the metal pipe wall to overheat or even burst. The above is the importance of the use of small and medium-sized industrial water softening equipment. There are also some simple introductions. I hope it will be helpful to you. You can always follow the environmental protection water treatment equipment company website so that you can grasp first-hand information.
Contact Person: Ms.Carrie Chan
TEL : (+86)020-39185731
E-MAIL : email@example.com
Whatsapp/Wechat : +86-13751887537
Water Treatment System Add:9A,Building 8,Lianfa Industrial Park , Luopu Street, Panyu District, Guangzhou City, China
Water Filter Cartridge Add:Zhangcun village,Daze town, Xinhui district, Jiangmen City, Guangdong, China
Sign up for our newsletter
Get the latest news and updates from the leaders in water treatment and process separation.