What should be paid attention to when installing small and medium-sized automatic pure water treatment equipment?
What should be paid attention to when installing small and medium-sized automatic pure water treatment equipment? Author: With more and more serious water pollution in economic development, more and more industrial enterprises selected on the basis of its own equipment on the plus ancillary equipment, small automatic water treatment equipment is one in which the popular choice of equipment . Different models and styles of equipment pose a lot of small problems for different enterprises to install. Installation is a seemingly simple problem, but there are some points of attention that we cannot ignore. The following introduces the points that should be paid attention to in the installation of small and medium-sized automatic pure water treatment equipment: 1. No special installation foundation is required. The foundation is horizontal and there is a gap from the wall. It can be arranged at the corners according to the actual situation. 2. The inlet and outlet pipes are connected by standard flanges or threaded connections and need to be fixed and supported. The valve body cannot be used for support to prevent stress. 3. A water pressure gauge should be installed on the inlet pipe. Flushing water is discharged when the equipment is running. Floor drains or drains should be installed nearby. The sewage pipe should not be longer than 6 meters. Do not install a shut-off valve. The outlet should not be higher than the valve body. The terminal opening (to avoid siphoning), the fewer elbows, the better . 4. If the inlet water pressure is lower than 0.2mpa, a pipeline pump must be installed. 5. The pipeline must be flushed before use to avoid impurities blocking the valve body and contaminating the resin. 6. Brine pipe: The brine tank should be as close as possible to the tank, and the brine pipe should be as short as possible. 7. Install a power distribution socket on the wall near the equipment, which should be equipped with a fuse (generally not a switch), and a good grounding is required. Of course, some specific situations require us to use them flexibly. Only by completing the installation procedures of small and medium-sized automatic pure water treatment equipment can the safe operation of small and medium-sized automatic pure water treatment equipment be guaranteed to the greatest extent.
Contact Person: Ms.Carrie Chan
TEL : (+86)020-39185731
E-MAIL : email@example.com
Whatsapp/Wechat : +86-13751887537
Water Treatment System Add:9A,Building 8,Lianfa Industrial Park , Luopu Street, Panyu District, Guangzhou City, China
Water Filter Cartridge Add:Zhangcun village,Daze town, Xinhui district, Jiangmen City, Guangdong, China
Sign up for our newsletter
Get the latest news and updates from the leaders in water treatment and process separation.