Why is the operating data of the industrial automatic pure water treatment equipment abnormal?
Why is the operating data of the industrial automatic pure water treatment equipment abnormal? Author: Today, industrial automatic water treatment equipment plays its important mission in the industry, many companies are inseparable from the production of industrial automatic water treatment equipment. The industrial automatic pure water treatment equipment has a desalination rate of more than 99%, and the water quality is pure and pollution-free, which meets the water needs of the majority of users. After the industrial fully automatic pure water treatment equipment is officially put into use, it is necessary to make operational records. Through these operating records, the operating status of the industrial fully automatic pure water treatment equipment can be grasped. Once data changes occur, effective analysis must be done. Determine the source of the fault. Let's take a look at how to analyze the abnormal operating data of industrial automatic pure water treatment equipment? First, analysis of the reasons for low product water resistivity When the product water resistivity becomes low, we can analyze and consider from the following three aspects. 1. Analyze the average current between the various modules and the actual current between them, the change of the pressure value of the concentrated fresh water chamber, and the operating data records in the recent period of time to analyze the reasons. 2. Analyze and test instruments: test instruments to see if the data is inaccurate due to instrument problems. 3. Analyze the influent parameters. Analyze the influent water quality, and check the raw water quality to see if the influent indicators have changed. 2. Reasons for the conductivity of the product water to be greater than the conductivity of the feedwater When this happens, stop the operation of the purified water equipment immediately, and check the reason to see if it is caused by the following points: 1. Whether there is a reversed module electrode . 2. Whether the concentrated water chamber enters the fresh water chamber in reverse. 3. Whether the pressure of the concentrated water chamber is greater than the pressure of the fresh water chamber. 3. When the current increases, the quality of the produced water drops. Reasons Check whether the industrial automatic pure water treatment equipment has membrane failure or damage. The above-mentioned situations are common data abnormalities in the long-term operation of industrial automatic pure water treatment equipment. You can use the above-mentioned contents as reference materials to understand the source of the problem and corresponding solutions.
Contact Person: Ms.Carrie Chan
TEL : (+86)020-39185731
E-MAIL : firstname.lastname@example.org
Whatsapp/Wechat : +86-13751887537
Water Treatment System Add:9A,Building 8,Lianfa Industrial Park , Luopu Street, Panyu District, Guangzhou City, China
Water Filter Cartridge Add:Zhangcun village,Daze town, Xinhui district, Jiangmen City, Guangdong, China
Sign up for our newsletter
Get the latest news and updates from the leaders in water treatment and process separation.