Why is the use time of RO membrane for medical ultrapure water equipment shortened?
Why medicine ultra-pure water equipment RO membrane usage time is reduced writer:? In the pharmaceutical industry water use is the most important, so water production equipment must meet the standards. When using medical ultrapure water equipment, RO membrane is the most important filter element in ultrapure water equipment. Its performance directly affects whether the effluent quality can meet the water requirements. The shortening of the membrane's use time will directly affect the performance of the medical ultrapure water equipment. Service life and operating cost. Then why is the RO membrane service time of medical ultrapure water equipment shortened? 1. The medical ultrapure water equipment needs to be shut down for maintenance. After the system is emptied, the gas will be quickly boosted without exhaustion when it runs again, and residual gas will be formed The air hammer damaged the membrane element. 2. Rinse with pretreatment water added with chemical reagents. Water containing chemical reagents may cause membrane fouling during equipment shutdown. 3. The reverse osmosis membrane of the medical ultrapure water equipment is not cleaned regularly, so it is necessary to master the cleaning method of the RO membrane in the medical ultrapure water equipment to clean the membrane elements regularly to ensure the stability of the performance. 4. The treatment effect of medical ultrapure water equipment pretreatment process becomes worse. 5. The pretreatment process of medical ultrapure water equipment has not been adjusted when the quality of raw water changes. The use of medical ultrapure water equipment requires RO membrane to avoid these problems. Once problems occur, corresponding measures must be taken to effectively solve them, so that the working performance of the RO membrane for medical ultrapure water equipment can be fully utilized to ensure the safety of ultrapure water equipment. reliability.
Contact Person: Ms.Carrie Chan
TEL : (+86)020-39185731
E-MAIL : email@example.com
Whatsapp/Wechat : +86-13751887537
Water Treatment System Add:9A,Building 8,Lianfa Industrial Park , Luopu Street, Panyu District, Guangzhou City, China
Water Filter Cartridge Add:Zhangcun village,Daze town, Xinhui district, Jiangmen City, Guangdong, China
Sign up for our newsletter
Get the latest news and updates from the leaders in water treatment and process separation.